|-5 - 60 °C
|Flaming loop test
The trunkings are available in lengths with a tolerance of ± 0.5% at 20 ° C.
They are resistant to aggressive and chemical environments. They do not resist UV radiation, they are not suitable for outdoor use.
The individual cables can be electromagnetically shielded by inserting a shield canal if necessary, to avoid interference. In the case of mounting the SK 40X33 (higher) shielding canal, it is not possible to use instruments with a larger installation depth, eg a surge arrester.
|Area with explosion danger
Electro-installation trunking (insertive, rectangular, halogen-free) and parapet canals with accesories can be installed in zones with explosion hazard of flammable gases (zone 2) and with the risk of explosion of flammable dusts (zone 22), installation must comply with EN 60079-14.
|Fire reaction class
|A1 - F
|Allows to install double-socket
|Possibility to connect the wall socket
|ČSN EN 50 085-1
|package - cardboard
|With protective foil